PMU Kg.Jawa Hyosung GIS Overhaul Project – PMU Kg. Jawa Hyosung GIS Overhaul at the Substation as part of 20-years OEM maintenance recommendation
GIS Overhaul Works: On-going
Another visit gone right was an achievement Universal Peak Sdn Bhd was proud about. The site investigation to the PMU Kilat (KLAT) Substation that was held on 27th January 2019. TNB was in the midst of doing their routine maintenance test and had failed their insulation resistance test. Further investigations performed by Hyosung’s supervisor led to identifying that this 25-years old operating substation is having a faulty ES Bushing B-phase. Upon submitting a report to TNB detailing the situation we had included our recommendation to do a replacement of the ES bushing. Once again for one of our valued Partners TNB and support from Hyosung’s supervisor, both our Project and Technical teams worked hand in hand to complete the Project.